Full Text Searchable PDF User Manual
4 Wire Optical Smoke Detector
4 Wire Optical Smoke + Heat Detector
Installation and User Manual
Publish Date: 15/4/2011
Before using the device read this manual carefully. Keep it
just in case of necessity.
Abide all the rules and precautions stated in the manual.
Follow all the instructions one by one.
Keep the devices away from water and moisture.
Do not energise the device above or below the given limits
of extreme hot or cold conditions.
C and +55
%95 at +40
Air flow limit:
Below 600 meters/min
Do not try to fix the device on your own, Removal of cover
may end up with electricity shock.
In case of any defect or malfunction, contact with your dealer
or with authorized service. All the technical interventions has
to be done by technicians of service company.
MALFUNCTIONS FOR TECHNICAL SERVICE
In case of any malfunction or below conditions contact with
your authorized service.
When Mains cable or the plug is harmed,
Contact of device with a fluid,
Exposure of rain and water,
Fell down of device or harmed outer cover,
Serious performance fall on the device,
Depending on the instructions stated in manual, if your
device not working properly, further usage or possible
wrong usage may cause other malfunctions . Contact
with your authorized service in such terms.
If the repair will be done by spare parts, to avoid fire,
electricity shock or any other hazardous conditions, Make
sure your service is using original parts or parts compatible
with your equipment.
To make sure if your device working properly and in safe
conditions or not demand service from your dealer to check
INSTALLATION AND CONNECTION
1. Remove the head of the detector attached to base by
turning it counter clock wise until you reach the short line
on the base(1),then pull it off(2).
2. Use at least 2 opposite ones from 4 of the screw holes
on the base to fasten it.
3. Do the wiring according to schematic shown below. The
order of cables do not make any difference. There is no
4. Place the detector head back. Make sure the short line
on head fits with long one on the base.
5. Energise the detector. If there is no alarm condition the
LED on detector flashes once every 10 secs to show it is
working at that moment. .
This test process captures both heat and smoke sensor
inside.To make a correct test, you need stable air flow at
70°C or visible smoke flow. (TFD 1450 only).
Visible smoke flow is enough for testing TFD1430.
1. If your panel has the test function ability. Start the test
2. Start the hot air flow and control the temperature
3. Let the air flow directly to the top of detector head which
covers thermistor. Detector will switch to alarm mode 30
seconds at most.
4. Reset detector from the panel.
5. For smoke test, allow smoke from a cotton wick or a test
smoke aerosol to enter the detector-sensing chamber
for at least 10 seconds.When sufficient smoke enters
the chamber, the detector will start the alarm.
6. After the alarm is active remove the source. Check if
the red LED on detector is active. Then reset the
detector from panel.
7. If the detector is not responding in 30secs and not going
in alarm mode,you must send it to service .
8. After the test is complete, system can be activated.
IMPORTANT NOTES ABOUT DETECTOR USAGE
Multisensor Works as combination of both heat and
smoke detector. At least one of them going alarm
mode is enough for it to warn (TFD1450 only).
To make sure both heat and smoke is working,
complete all steps on the test.
The recommended minimum requirement for the
detector maintenance consists of an annual
cleaning of dust from the detector head by using a
vacuum cleaner cleaning program should be
conformance with EN 54-7:2000 and EN 54-5:2000
2 / 4
TFD 1430 NC
9 - 15
-10 ~ 50
Cream color UL 94
TFD 1450 NC
DO NOT TRY TO REMOVE THE DETECTOR FROM
THE PLASTIC COVER. THIS ASSEMBLY IS SEALED
FOR YOUR SAFETY. USERS MUST AVOID
INTERVENTION. OPENING THE DETECTOR HEAD
WILL REMOVE WARRANTY.
Teknim Elektronik San. ve Tic A.
Address : Organize San. Böl. 1. Cad.
. Mrk. Bina No:1 Kat:2,
No:24, 25, 29 Dudullu. PK:34776 Ümraniye/
Tel: +90 216 499 06 80
Fax: +90 216 499 06 79