Related Product Video
Full Text Searchable PDF User Manual
P/N7121702 Rev. A
Fire Safety & Security Products
Teclado numérico LC
Klávesnice s LCD displejem
Before starting to install and work with this device, please read the Safety
1 Scope of delivery:
• IKP6-03 LCD keypad
• Screws (a)
• Plugs (b)
• Tamper screw (c)
2 Removing the cover
Loose the retaining screw.
Lift off the cover from the base.
3 Mounting the base
Use only the screws and plugs supplied.
Mount the base (inside up) to the wall using the build in spirit level (a).
If necessary adjust the distance to the wall of the back tamper contact (b)
with the included tamper screw.
4 Connecting up
Disconnect the control panel from power (main and battery).
Connect the BUS from the control panel to the IKP6-03 unit on the terminal
blocks, as described in the Installer Manual.
Reconnect the control panel to power: the display and the keys will light up if
If the lights are fast flashing, a connection failure had happen.
Please recheck connection.
5 Replacing the cover
Hook the cover onto the top of the base and press into position.
Screw in the retaining screws.
The user communicates with the alarm system via the keypad. The keypad
displays continuous information about the status of the alarm system and allows
the user to operate the system in different modes, change settings and program
users' access codes.
The keypad also keeps a log of events, which can be displayed subsequently on
demand when reviewing system activities and used to analyze system
performance for diagnostic purposes.
As an additional comfort feature a temperature indication is included in the display,
which shows the temperature around the installed keypad.
The LCD display shows all the information
required for trouble-free operation of the system.
These keys are used to arm the system, enter
commands to alter system settings, or scroll
through the display.
These keys are used to enter codes, change
descriptions of zones, or for programming.
100 mA (backlight on) -
40 mA (backlight off)
9 - 16 V
Blue back light
For key illumination
-10 - +50 °C
145 x 126 x 22 mm
12 V DC (Via E-BUS)
KP 2 x 16 characters
recommend to use shielded cable like Kat5.
Max. bus length
Tested up to 200m
Complies with: EN 50130-4+A2, EN61000-6-3, EN55022 + A1+A2+Kl. B,
EN50131-1, EN50131-3, Security Grade II, Environmental Class II
For more detailed instructions please refer to the manuals which can be
downloaded from internet: www.siemens.com/homesecurity